Results 1 to 1 of 1
Plumbing & Plumbers Forum - Croppie's Balancing Thread.
Croppie's Balancing Thread.Discuss Croppie's Balancing Thread. at UK Plumbers Forums; How To Balance Radiators Tool List: Radiator-bleeding key Lockshield valve adjuster or adjustable spanner Screwdriver Digital thermometer or multimeter with thermometer function 1. Make sure all the radiators have been ...
- 13-01-2016 #1
- Join Date
- Jul 2010
- Lurking somewhere, generally up to no good........
- Thanked 1,834 Times in 1,672 Posts
Croppie's Balancing Thread.
How To Balance Radiators
Lockshield valve adjuster or adjustable spanner
Digital thermometer or multimeter with thermometer function
1. Make sure all the radiators have been bled. Turn off the central heating and allow the radiators to cool.
2. Familiarise yourself with the valves. The lockshield will usually have a push-on cap or one that is secured with a screw through the top. Remove it.
3. Older models will have a wheelhead valve on the other side — used to turn the radiator on/off.
4. Newer radiators will have a thermostatic valve instead of a wheelhead valve.
5. Open up the valves on all the radiators in the house by turning them anti-clockwise.Wheelhead and thermostatic valves can be turned easily by hand, but the lockshield will need a plastic adjuster to open it up. These come with new lockshield valves. A spanner will also do the job.
6. Turn the central heating back on and note down the order the radiators heat up. Those nearest the boiler normally get hot first. If you’ve got a lot of radiators, get assistance. Turn the heating off and wait while the radiators cool down. You will also need check your DHW Cylinder primaries to ensure that the flow heats up at about the same rate as the heating flow. You should have a throttle valve on the primary return.
7. When the radiators are cool, switch the heating back on and go to the first radiator on your list. Turn the lockshield valve clockwise until it is closed and then open it by a quarter of a turn. Once the radiator has warmed up, take a temperature reading at the pipework leading to one of the valves.
8. Now take a temperature reading at the pipework leading to the other valve and open the lockshield valve gradually until there’s a 12°C difference between now and the reading you took in step 7 (allow a couple of minutes after each adjustment for the temperature to change). The temperature figures indicated in the last step and this one are relevant to the radiator shown – don’t take them as any kind of optimum figure – it’s the 12°C difference in temperature at the valves that counts. Next, check the rest of the radiators in the system following the order in the list. The further you move away from the boiler, you’ll find the lockshield valve will have to be opened more. The last radiator may need to have the lockshield valve fully open to work at full efficiency. Your radiators are now balanced and should work perfectly.
Getting A Temperature
A key part of this job is measuring the temperature difference across each radiator. Specially designed thermometers that strap round the pipes at either end of the radiator are available to buy or hire, but it’s not really necessary to use these. You can get away with a single digital thermometer — it just means that you can’t take simultaneous readings and you’ll have to move from one end of the radiator to the other.
Digital thermometers are available from around £10. Alternatively, some digital multimeters have a temperature sensor function. A digital multimeter with temperature function costs from £25 and can also be used for taking electrical readings and checking continuity in wires, among dozens of other functions.Propino Tibi Salutem! Usque ad Mortem Bibendum!
(By the way, I'm commercial!)
Carbon Monoxide can be produced when ANY fuel is burnt, including oil, gas, wood and coal.
GSR? Want gas safety or boiler repair advice? We will check out that you're genuine via the gas safe website, so please don't be offended when we ask for your details. DIYers, odd job people and have a go heroes need not apply.
- By Biilee in forum Plumbing ForumReplies: 10Last Post: 17-09-2014, 07:51 PM
- By casey_pearce in forum Central Heating ForumReplies: 10Last Post: 27-02-2013, 06:31 PM
- By Dave in forum Links, Forum Updates, News and Site SuggestionsReplies: 0Last Post: 01-12-2011, 06:49 PM
- By stecorcoran83 in forum Central Heating ForumReplies: 2Last Post: 17-01-2011, 10:39 PM
Visitors found this page by searching for:
Nobody landed on this page from a search engine, yet!